High-performance DriveTOSVERT VF AS3 (～315kW)
CompactTOSVERT VF S15 (～15kW)
for HVACTOSVERT VF FS1 (～30kW)
Compact. SimpleTOSVERT VF nC3 (～3.7kW)
Number Categories Applications
Member service Top
Company Information Top
Note 1) *** in the type-form are numeric character. Please refer the "Selection of braking resistor" in each inverter catalogue ( VF-AS1, VF-PS1, VF-S15, VF-S11 ). Note 2) The rating shows the synthetic resistor value (Ohm) and the synthetic resistor power (Wait). The word in the parentheses shows the composition of resistor elements. Note 3) The allowable continuous regenerative power differs on the resistor value or power tolerance. Please refer the "Selection of braking resistor" in each inverter catalogue( VF-AS1, VF-PS1, VF-S15, VF-S11 ).
Note 1) In case of 400V class, please apply the 200V to the operation circuit by using control transformer or 200V power supply. Note 2) Please twist the wire by 10 cm pitch. The distance between resistor power wiring and the control wiring should be over 20 cm. Note 3) In case of TOSHIBA thermal relay, please make a short circuit with 8 mm2 wire between the 2/T1 and 6/T3 of the thermal relay. Note 4) In case of VFAS1 200kW or larger, VF-PS1 250kW or larger, it is necessary to install a braking unit (PB7 series).
Note 1) The braking resistors are designed for indoor type. Please use them with drip cover in case of water drop. But please note it is not for water proof protection type. Note 2) A,D,E,F are the dimensions of standard type. A1,D1,E1,F1 are the dimensions of those with drip cover type.